Parameters of low-voltage cable
1: Standard GB/T 12706.1-2008
2: Detailed description
? Conductor: Compacted or un-compacted copper or aluminum
? Insulation: Cross-linked polyethylene or polyethylene
? Filler: Filler yarn
? Packaging: Wood shaft or packaging bag, depending on your requirement
? Outer sheath: Polyethylene
? Armoring: Fine steel wire armoring or steel tape armoring
3: Standard sectional areas: 10mm2, 16mm2, 25mm2, 35mm2, 50mm2, 70mm2, 95mm2, 120mm2, 150mm2, 185mm2, 240mm2, 300mm2, 400mm2.
Type Name Application
YJLV Cross-linked polyethylene-insulated, PVC-sheathed power cable
Cross-linked polyethylene-insulated, PVC-sheathed aluminum power cable Be laid indoors or outdoors, can bear certain pulling force, but cannot bear external mechanical force.
YJLV22 Cross-linked polyethylene-insulated, steel tape-armored, PVC-sheathed power cable
Cross-linked polyethylene-insulated, steel tape-armored, PVC-sheathed aluminum power cable Be applicable to direct burying underground, and can bear certain external mechanical force but cannot bear large pulling force.
YJLV32 Cross-linked polyethylene-insulated, fine steel wire-armored, PVC-sheathed power cable
Cross-linked polyethylene-insulated, fine steel wire-armored, PVC-sheathed aluminum power cable Be laid in rainwater or in the area with high drop, and can bear external mechanical force and equivalent pulling fore.
Note: Add ZC to the original model of flame-retardant cable of the Company, NH to fire-resistant cable, and WDZN to low-smoke, halogen-free, flame-retardant and fire-resistant cable.